The Diver 6 pumps are very easy to install and they do not require any configuration. We recommend you read the instruction manual of the Diver 6 (also available in our DNA software) for useful information for use, maintenance and installation and the procedure for using the pump in manual or automatic mode.
Insert the plug of the power cable into a suitable power socket.
The float switch starts and stops the pump automatically. The water level that prompts the starting and stopping of the pump can be adjusted by changing the length of cable of the float between the holder and the float.
N.B. The length of the float cable must never be shorter than 10 cm.
a) The float switch must be lifted in order to start pumps with a float.
b) For pumps without a float, insert the plug.
Before starting the pump, check that:
The voltage and frequency specified on the pump’s data plate coincide with those of the available power supply;
- there are no signs of damage to the pump or its power cable;
- the electric connection is made in a dry place, protected against any risk of flooding;
- the electric system is complete with a residual current circuit-breaker (I ∆ ≤ 30 mA) and an efficient earthing connection;
- Any extension cords must comply with the requirements of regulation DIN VDE 0620.